Corrupt Eskom staff may be sabotaging power stations — De Ruyter
Eskom CEO André de Ruyter says that Eskom is investigating suspicious circumstances surrounding the breakdowns of several power stations. Paraphrasing a principle known as Hanlon’s Razor, De Ruyter said he always tries to assume good faith.
“My fundamental point of departure has always been not to attribute to malice what can be explained by incompetence,” the Eskom chief said in an online briefing with journalists.
However, Eskom recently had an incident where three units at Matimba power station went down simultaneously. De Ruyter explained that a team had been working on the station’s dry cooling fans when they dropped an extension cord onto the unit 2 transformer.
This caused a flash, which tripped the station board and shut down all cooling to units 1, 2, and 3, leading to all three shutting down. We have difficulty in believing that this is entirely coincidental, so we have dispatched a forensic team to site,” said De Ruyter.
“We will also be deploying additional security to site in order to ensure we can protect our assets.”
De Ruyter said they also had a close shave at Lethabo power station on Wednesday night when a distribution tower collapsed.
He explained that two distribution lines power Lethabo’s coal conveyors.
“These lines are each capable of carrying the full load. There is double redundancy,” explained De Ruyter.
At around 18h00, just before the evening peak, the tower for the one line collapsed onto the other line, wiping out the station’s double redundancy.
“Thanks to some very nimble footwork by our distribution management team, they were able to devise a third supply from the Free State,” De Ruyter said. This took a bit of engineering, and by 03:00 this morning [Thursday], they were able to restore supply and managed to keep coal supply to Lethabo going.”
In other news – Gomora 2 Teasers – December 2021
Coming up on Gomora this December 2021: Ntokozo refuses to back down on his pursuit for true love.
Teddy’s way of dealing with grief concerns Zodwa. Phumlani scores points on Buhle and receives good news. Learn more